CO2 Multi Sensor System
The CO2 Multi-Sensor System is designed to detect Carbon Dioxide (CO2) levels in the ambient air to protect employees, workers, and establishments.
CO2 monitors are required in most jurisdictions by code and regulation.
The CM-7000 features both audible and visual alarms as well as the ability to configure sensors independently including the 4 relays that are triggered at 5,000 TWA, 5000 ppm, 1.5% CO2, and 3% to meet OSHA/NIOSH standards including local fire codes.
Users may configure modules (sensor, horn/strobe, and key switch) from any tablet either in direct connection or through daisy-chaining modules together. You may not exceed 12 horn/strobe modules on any string.
With the CM-7000, you can ensure that you and your employees are safe and protected, and should an incident occur rely on the CM-7000's ability to trigger an exhaust fan or send an immediate alarm to the fire department or monitoring company.
Please note: *High concentrations of carbon dioxide in confined spaces are dangerous, and may lead to negative health problems ranging from fatigue, asphyxiation or even fatality, if not properly monitored.*
- 8" Touch Screen Display Panel
- 12 easily addressable CO2 Sensors
- 100% Clean, Modern Appearance - All cables can be hidden
- Customer Configurable Alarm and Notification Settings
- Mute Push Button to temporarily mute audible alarms
- Integrated Speaker and USB port
- Meets NFPA, IFC, and NBIC Requirements
- Meets OSHA and NIOSH TWA Standards
- Meets all local municipality inspection codes and requirements
CM-7000 - CO2 Multi-Sensor System - Includes: (1 Main 8" Touchscreen Control Tablet, 2 Sensor Units, 2 Horn Strobes, Mounting Hardware, Cables, Power Supply and Safety Signage.)
CM-7001 - Sensor Unit and Horn Strobe Add On
CM-7002 - Reset Unit Add On
CM-7003- Sensor Unit Add On
CM-7004- Horn Strobe Add On
- Restaurant and Food
- Breweries and Wineries
- Beverage Dispensing
- Medical and Scientific
- Measurement Range: 0-5% (0-50,000 ppm)
- CO2 Measurement: NDIR (Non-Dispersive Infrared
- Alarms: 5,000 TWA, 5,000 ppm, 1.5%, and 3% (default)
- Custom Alarms: 1%, 2%, 2.5%, 3.5%, 4%
- Measurement interval: 2 seconds (0.5Hz)
- Operating Temperature: 32-122°F (0-50°C)
- Calibration: Zero with Nitrogen or Factory Calibration
- Connections: Input/ Output/ Strobe - CAT5 8 pin connector
- Sensor Life Expectancy: > 15 years
- Power Supply: 110-220 VAC 50/60 Hz to 12 VDC Power Adapter
- Power Input: 4.5-5.25 VDC
- 24VDC hard-wired power option
- Power Consumption: 300mA peak, 30mA average
- 6VDC battery backup connections
- Horn Strobe: 90-120dB 3KHz, 110 cD
- 1 year - See CO2Meter Terms and Conditions
CM-7002 - Reset Unit Add On - the reset unit add-on provides a unique push-button and key switch to mute and reset latch for all sensors connected to the tablet. Click here, to order.
CM-7005 Main Tablet Only - 8" inch touch screen control panel. Contact us, to order.
CM-7006 - Mini Display Tablet - designed for remote display only. Contact us, to order.
CO2 Storage Safety Strobe Tower- designed to provide a flashing indicator, and audible alarm with any of our CM-7000 systems. Click Here, for More.
SV-1027 Solenoid Safety Shut Off Valve - designed to be utilized with our CM-7000 CO2 Multi-Sensor System, and can be directly wired to the SV-1027 24/DC safety shut-off valve via main tablet or sensor unit relays. Contact us, for more info.
The Tablet design is awesome. As it is daisy-chainable; the number of ports is perfect. It’s an elegant physical design, and its’ ability to adapt to different configurations is wonderful. The minor flaw? The necessity for power boosters. That necessity is, I am sure, directly related to the POE design and electrodynamic requirements of signal dropoff; yet the booster makes it slightly ungainly; though I understand the need for it. By putting the strobes/horns together--- it saves a step and makes it a time-saving bonus. Well thought out and I love the interface!
From the minute I met Josh at the convention center and he walked me through the CM-7000 I knew it was the unit for me. I had to fight to get it and be an early adopter and I am glad I did. At the time I saw it I understood the advantages of expandability and CO2meters commitment to make that happen. What I did not know..is what I did not know at that time......City building departments are not standardized! And they can change their mind! We had submitted plans and had been approved by the Building Department but when the first Fire Inspector showed up they added requirements to the system. To put in perspective we more than doubled the number of sensors and alarms. The added items were quickly supplied by Rosie and supported by Ben. I can only imagine how much difficulty it would have been if I had purchased a more limited system....if possible at all.